Thermal Expansion Tanks
One of the physical properties of water is that the volume increases when it is heated, such as with your hot water tank. To appreciate how much it will expand; the water in a typical residential hot water tank holding 40 gallons will increase by about a half a gallon when heated to 70 degrees Fahrenheit. However, if the water is restrained from expanding by the plumbing the result will be an increase in pressure. The resulting pressure can be enough to damage your hot water tank or plumbing. Some people might have noticed that they don't have a thermal expansion tank and have never had any such problems. If there is no check valve in your meter pit then your plumbing is unrestrained. The volume expanse brought about by your hot water tank will simply expand back through the meter and into the water main. Because the water is unrestrained, there will be no increase in pressure. For houses that do have a check valve in the meter pit the potential for trouble is much greater, but you may still go several years without experiencing any problems. There might be several reasons for this: 1. While your hot water heater is running, the pressure in the tank and plumbing is increasing slowly. If at any time you open a faucet, such as to fill a glass with water, the pressure is instantly relieved. 2. The increasing pressure might cause a small leak at a fixture, such as a toilet or faucet, causing it to run or drip until the pressure is relieved. 3. If you stop using water before the hot water heater is done running the pressure may still increase, but not by enough to be noticed. Hot water tanks contain a pressure relief valve to protect them from rupturing under such a scenario. The relief valve is typically set at 150 PSI, although this may vary among manufacturers. The valve opens when the tank pressure reaches the valve set point. After enough water has passed through the valve the pressure in the tank drops and the valve closes again. The concern of depending on these valves is that sometimes in older hotwater tanks they might be plugged with scale or corrosion and not function properly. For this reason, a thermal expansion tank is recommended. The basic objective behind a thermal expansion tank is to give the expanding water a place to go so the increase in pressure brought about by heating the water will be controlled. It is important to note that even with a properly selected and installed thermal expansion tank the plumbing pressure will still increase, but not by enough to cause a failure in the plumbing system.